Learn about the technologies behind the Internet with The TCP/IP Guide!|
NOTE: Using robot software to mass-download the site degrades the server and is prohibited. See here for more.
Find The PC Guide helpful? Please consider a donation to The PC Guide Tip Jar. Visa/MC/Paypal accepted.
|View over 750 of my fine art photos any time for free at DesktopScenes.com!|
The line-interactive UPS uses a totally different design than any type of standby UPS. In this type of unit, the separate battery charger, inverter and source selection switch have all been replaced by a combination inverter/converter, which both charges the battery and converts its energy to AC for the output as required. AC line power is still the primary power source, and the battery is the secondary. When the line power is operating, the inverter/converter charges the battery; when the power fails, it operates in reverse.
The main advantage of this design is that the inverter/converter unit is always connected to the output, powering the equipment. This design allows for faster response to a power failure than a standby UPS. The inverter/converter is also normally fitted with circuitry to filter out noise and spikes, and to regulate the power output, providing additional power during brownouts and curtailing output during surges.
The line-interactive UPS is an improved design that is commonly used in units for home and business use, available in sizes up to 3,000 VA or so. It is superior to the standby UPS, but it still has a transfer time, and thus does not provide protection as good as the online UPS.
Next: Online ("True") UPS